The V4 Series is an electric motor actuator with end of travel limit switches which stop the motor in each direction.
In this video the V4 Series actuator is shown mounted on an Assured Automation 26 Series Ball Valve.
The V4 Series comes with external wire leads for ease of wiring. The housing cover never needs to be removed.
To Open the actuator “counterclockwise” (CCW):
locate the white wire #1 and red wire #5 for CCW rotation. When power is applied to 1 & 5 the actuator will turn CCW until it reaches the internal limit switches and shuts off.
To Close the actuator “clockwise” (CW):
Locate the white wire #1 and the black wire #3 for CW rotation. When power is applied to #1 & #3 the actuator will turn CW until it reaches the internal limit switches and shuts off.
The blue wire #2 will have power on it when you reach the full closed position.
The yellow wire #4 will have power on it when you reach the full closed position.
If these feedback switch wires are not going to be used, they must be properly isolated to prevent short or shock.
The wiring diagram can be found on our website (https://assuredautomation.com) and inside the actuator cover.
Thank you for viewing.
From your friends at Assured Automation
For any other questions contact us online or call toll free at 1-800-899-0553.